The thermostat as a all in one temperature controller, users can be flexibly set for air conditioning, floor heating, or ventilation controller. Among them: as the air conditioning temperature controller, you can choose to set as one way three line two control valve, or one way three line one control valve control single cooling or heating, or two way two line valve control dual cooling and heating, support high, medium, low, automatic wind speed, local room temperature detection; When used as the floor heating thermostat, it can support the maximum 2.5A load output control; As a ventilation controller, it can support high, medium and low wind speed control.
the thermostat can automatically request the gateway synchronization time, support the reporting of the actual working status of cold and hot valves and fans, and support linkage control.
1. Local Control
a) ON/OFF：Hold down the open key for 1 second to switch the machine on and off.
b) Wind speed control: press the function button to switch the low speed, medium speed, high speed and automatic mode under the working mode of air conditioning and ventilation.
c) Temperature control: press the up or down button to adjust the set temperature under the working mode of air conditioning and floor heating.
d) Air conditioning mode selection：Under the working mode of air conditioning, keep pressing the function key to cycle switch cooling, heating and ventilation in the mode of air conditioning.
2. Local menu
a) When the machine is off, keep pressing the function key for 1 second to enter the local menu for setting; In the local menu setting mode, press the function key to select the menu item, press the up and down key to modify the setting parameters; When the setting is completed, press the power button to save the parameters.
b) Menu function parameters are described below：
bF- Restore power down
Set temperature ceiling
Set temperature limit
Low temperature protection
Temperature limit of external sensor
Valve start temperature difference
Air conditioning fan maintenance
Air conditioning control
Display brightness mode
OF-Turn off screen
Update filter time
3. Wireless network registration/removal
a) Network registration: after the user starts the registration status of the main control gateway, press the "up" and "down" keys for 2 seconds at the same time in the shutdown state to start the network registration. During the registration process, the wireless status icon flashes.
b) Network removal: After the user starts the removal state of the main control gateway, press the "up" and "down" keys for 2 seconds at the same time in the shutdown state to start network removal..
c) In the unregistered state, the wireless status icon keeps flashing slowly.
4. Wireless network linkage
a) This product supports 4 groups of device association. The first group can be associated with 1 device, and each other group can be associated with up to 5 devices.
Group 1: Thermostat status report;
Group 2: Switch on/off the device when the corresponding thermostat is on.
1. Parameter number：01 – set all in one service mode.
Bits Length：1 byte
01 – Air conditioning thermostat working mode；
02 – Floor heating thermostat working mode；
03 –Ventilation controller operating working mode.
The network should be removed and added again after the device's working mode is modified.
2. Parameter number：02 – Set and temperature control address.
Bits Length：1 byte
Parameter values： 0~255，0x00（default）.
3. Parameter number：03 – reserve.
4. Parameter number：04 – Set power on switch machine mode.
Bits Length：1 byte
Parameter values： 0~1，0x00 Electricity power off（default），0x01 Electricity power on.
5. Parameter number：05 – reserve，set Time Zone Number.
6. Parameter number：06 – Set the temperature controller specified parameters.
Bits Length：4 byte
Parameter values： Byte 1, 2 for the thermostat register address; Bytes 3 and 4 set the parameters for the corresponding registers. See multi-function thermostat control register parameter table for details.
1. In the process of use, if you encounter thermostat failure, please contact the supplier in time, do not disassemble and repair privately, so as to avoid damage.
2. Switch housing has heat dissipation through hole. When cleaning, pay attention to avoid water vapor penetrating into the box cover, which may lead to circuit damage and short circuit.
Cold valve single way
Hot valve single way
maximum 2.5A @220VAC
Fan single path
868.4 MHz – China/Europe
908.4 MHz – America
921.4 MHz – Australia
869.2 MHz – Russia
Indoor straight-line distance is 30 meters
Outdoor distance is 50 meters as the crow flies
Temperature Controlling Range
86 x 86 x 34 mm
59 x 61 x 23 mm
Z-Wave supports commands
Generic Deice Type =
Specific Device Type =
Support Command Class =
Tel: +86 577 6266 1999 Fax: +86 577 6266 1113 Email: email@example.com
Copyright © 2017 TKB TECHNOLOGY All Rights Reserved. XML